determine the amount of fuel in the bowl. When
(2) Close the latch the burner access door.
there is just enough fuel to wet the tip of the wick,
( 3 ) Turn the burner fuel line shutoff valve to
c l o s e the burner fuel line shutoff valve by turning
t h e open position.
the handwheel clockwise.
h. Move the burner air duct damper pull rod to
e. L i g h t t h e w i c k w i t h t h e f r i c t i o n i g n i t e r o r
the operating position by gradually releasing the
p u l l rod until a stable fire with proper flame has
f. Pull out the air duct damper pull rod (fig. 1-1
and 2-4) to close the burner air duct damper (which
w i l l shut off the forced air blast to the burner) and
If the burner fails to Iight properly, relight it at
t h e n hold it in that position (fig. 2-4). Immediately
once, unless 2 minutes or more has elapsed. In this
case, fuel may be overflowing from the vaporizer
i n s e r t the lighted wick or torch into the burner pot
tube, and the burner fuel line shutoff valve must
u n t i l it contacts the bottom of the pot and ignites
be closed and no attempt must be made to relight
the burner for at 5 minutes. During this 5
minutes, keep the engine running and the burner
Exercise care to keep the face away
air duct damper open to aid in evaporating the
excess fuel in the burner. After 5 minutes has
from the burner access door when
elapsed, proceed to light the burner again, using
lighting the burner.
the lighting instructions in a through h above;
g. Continue to hold the damper pull rod out and
t h e n move the burner air duct damper to
proceed as follows:
( 1 ) Remove the torch lighter and extinguish it
b y holding the wick in or over the exhaust stack.