4-23. DRUM FILL ADAPTER ASSEMBLY, TYPE II. (CONT)
Repair by replacing defective parts.
Use sealer on pipe threads before installation.
Attach cover (9) to nipple (10) by turning clockwise.
Attach double male pipe to supply side.
Install adapter pipe (8) in block (7) by turning clockwise.
Install block (7) and adapter pipe (8) in nipple (10) using two screws (5) and four washers (6).
Install pipe connector (2) on adapter pipe (8) and install extension adapter (1) on pipe connector (2).
Install two male connectors (3) in nipple (10) by turning clockwise. Replace fuel lines or caps (4).
SECTION VI. PREPARATION FOR STORAGE AND SHIPMANT
4-24. SPECIAL INSTRUCTIONS FOR ADMINISTRATIVE STORAGE
Placement of equipment in administrative storage should be for short periods of time when a shortage of maintenance
effort exists. Items should be in mission readiness within 24 hours or within the time factors as determined by the direct-
ing authority. During the storage period, appropriate maintenance records will be kept.
Before placing the equipment in administrative storage, current preventive maintenance checks and services should be
completed, shortcomings and deficiencies should be corrected, and all Modification Work Orders (MWO) should be
Change 2 4-56