ORGANIZATIONAL MAINTENANCE INSTRUCTIONS
Section I. SERVICE UPON RECEIPT OF MATERIAL
4-1. Inspecting and Servicing Equipment
a. Visually inspect equipment for any damage which may have occurred during shipment.
b. Inspect heater assembly for signs of damage, missing parts, paying particular attention to crushed, broken or
loose roof jack assembly and circulating fan.
Refer to paragraph 2-3 for information on installing this equipment.
Section II. MOVEMENT TO A NEW WORKSITE
4-3. Dismantling for Movement
a. Remove rain cap from top of stove pipe.
b. Remove hood by straightening anchor straps and removing pin from sides. Lift off hood and insect screen.
c. Remove joints of stove pipe from damper, pipe shield, and roof flashing. Remove elbow and draft regulator tee.
d. Straighten and remove flashing and collar assembly from roof. Straighten tabs and remove pipe shields.
e. Unplug cord assembly from electrical outlet and remove fan assembly.
f. Straighten tabs on damper assembly and remove damper assembly from ceiling.
g. Be sure no fuel remains in heater or fuel control valve. Clean stove pipe, elbow, tee and heater of all loose
4-4. Reinstallation after Movement
Reinstall according to installation instructions given in paragraph 2-3.
Section III. REPAIR PARTS, SPECIAL TOOLS AND EQUIPMENT
4-5. Tools and Equipment
Tools and / or equipment authorized for the space heater are listed in the repair parts and special tool list, appendix C of
4-6. Special Tools and Equipment
No special tools or equipment other than those listed in section III, appendix C are required by organizational
maintenance personnel to maintain the space heater.
4-7. Maintenance Repair Parts
Repair parts and equipment are listed and illustrated in the repair parts and special tools list covering organizational
Section IV. PREVENTIVE MAINTENANCE CHECKS AND SERVICES
The necessary preventive maintenance checks and services to be performed by organizational maintenance personnel
4-9. Monthly and Quarterly Preventive Maintenance Checks and Services
Table 4-1 list those things that organizational maintenance personnel must
do on a monthly
or quarterly basis
keep the space heater functioning properly.