(3) Disconnect the cable wires from the thermostat switch. Remove the attaching hardware used to secure the
thermostat to the enclosure wall. Disconnect the ground lead from the thermostat, and remove the thermostat.
(4) Installation of a new thermostat is the reverse of removal. Be sure to use 16-gauge, 3-wire (red, black, green)
electrical cable per MIL-W-16878D. Ground the cable shield to the room thermostat mounting screws.