Table 2-1. Controls and Indicators-Continued
Control or Indicator
Disconnects power if short circuit occurs. Press to reset.
Controls air intake louvers to attain optimum air flow.
Heat output is constant when heater Is operating. Raising
thermostat setting does not heat enclosure faster. Set ther-
mostat only to temperature desired.
For selecting temperature desired in enclosure. Rotate until desired
temperature is aligned with index mark.
Connection for external source of 120 V ac, 50/60 Hz electrical power.
Connection for plugging in external electric fuel pump,
Connection for plugging in remote thermostat which controls heat of