3-29. POWER CABLE ASSEMBLY MAINTENANCE Continued.
Army cable P/N 13039-102 is compatible with the Distribution Illumination System, Electric
(DISE). Listed in Appendix D is a plug and receptacle for use with non-DISE, 20 ampere circuit
and 5/8 inch power cable.
(2) Repair of Army Cable P/N 13039-102 consists of replacing damaged parts with new parts.
(a) Cut strap (3) from connector plug (2) and remove cover assembly (1).
Sleeve assembly (4), screws (9), saddles (10), and clamp (1 1) is supplied as an assembly. If any
components are defective, replace assembly.
(b) Remove screws (9) and remove saddles (10).
(c) Remove sleeve assembly (4) from clamp assembly (11).
(d) Slide clamp (11), insulation tubing (12), rubber bushing (8), grommet follower (7) and grommet (6) from
(e) Unscrew connector plug (2) from sleeve assembly (4) and cut conductor wire.
(f) If identification strap (16) is defective, cut off.
(g) If terminals (13), (14), or ( 15) are defective, cut off defective terminals from conductor wires.
(h) Strip 8 inches of insulation from cable (17) end to expose three insulated conductor wires.
(i) Strip .25 inch of insulation from each of the insulated conductor wires.
(j) Crimp terminals (13), (14), or (15) onto the insulated conductor wires.
Crimp terminal (13) onto two green (ground) wires.
(k) Position identification strap (16) over cable (17) and pull point ends through strap holes to secure
identification strap (16) to cable (17).
3-86.4 Change 3